Halting Airborne Infections at Nemours Childrens Hospital.
Nemours Childrens’ Clinic in Jacksonville, Florida sealed its air duct system using Aeroseal duct sealing to improve HVAC airflow and ensure germs are removed.
Duct Sealing Critical to Halting the Spread of Airborne Infections at Nemours Children’s Clinic: Aeroseal® Used to Seal Exhaust Ventilation System and Ultimately Gain Control of Airflow in Older 11-story Medical Facility
There had been so many retrofits and extensions added to the ventilation system at Nemours Children’s Clinic in Jacksonville, Florida that engineers weren’t sure where their airflow problems were coming from. What they did know was that negative pressure and inadequate ventilation throughout the 30+-year-old building could support the spread of nosocomial infections. Their first steps in taking control of the situation was to seal the leaks in the exhaust shafts located on each floor and then seal the main shaft running down the length of the 11-story building.
HVAC Contractors: Carrier Corporation Aeroseal
Contractors: Aeroseal Southeast
Property Name: Nemours Children’s Clinic
Type: 11-story outpatient medical facilities
Goal: Improve airflow; reduce the risk of nosocomial infections
Before Aeroseal: Total system leakage: 4,912 CFM*
After Aeroseal: Total system leakage: 723 CFM Results: 85% reduction in leakage.
*Cubic feet per minute
Project: Nemours Children's Hospital
Location: Jacksonville, Florida USA
Air Conditioning System
Aerosealing the entire children’s clinic took less than 30 days to complete. The difference it made to the efficiency of the exhaust system was immediate and obvious. With the ductwork effectively sealed from the inside, engineers were able to accurately analyze the system and upgrade it with regulating dampers and other flow-adjusting technologies. Now the building’s exhaust system is optimized at all times. The bottom floors are as well ventilated as those on the top. Most importantly, the air being exhausted is coming from the rooms and common areas that need it; contaminated air is being removed from the building. As an added bonus, the clinic is able to run its exhaust fan at a fraction of the power that was previously needed, saving the clinic substantially on its energy costs.
“In order for a hospital to be clean, you have to manage the building’s airflow. By aerosealing the exhaust shafts we ensured that the right amount of stale and potentially infectious air is being adequately and continually removed from the building.”
– Derrick Rhodes, president, Aeroseal Southeast
“Exhausting air from a leaky ventilation shaft is like using a straw with holes in it. No amount of force is adequate to effectively ventilate the bottom floors of the building. Now, after sealing the leaks with Aeroseal, all floors are getting the ventilation they need. As a side benefit, we were able to dramatically reduce the speed of the exhaust fan, which has resulted in substantial energy savings for the clinic. With the ductwork effectively sealed, we are now able to take additional steps to optimize the entire exhaust system. ”
– Chuck Boynton, areas project manager, Carrier Corporation
NEMOURS CHILDREN'S HOSPITAL, JACKSONVILLE, FL
“after sealing the leaks with Aeroseal, all floors are getting the ventilation they need. As a side benefit, we were able to dramatically reduce the speed of the exhaust fan, which has resulted in substantial energy savings for the clinic.”
Chuck Boynton, Areas Project Manager, Carrier Corporation